This document is an American Water Works Association (AWWA) standard. It is not a specification. AWWA standards describe minimum requirements and do not . Awwa C R16 Encoder-type Remote-registration Systems for Cold-water Meters [Not Available] on *FREE* shipping on qualifying offers. All specifications meet or exceed the latest revision of AWWA C . All meters shall be equipped with encoder remote registers per AWWA C and shall.
|Published (Last):||9 December 2004|
|PDF File Size:||14.91 Mb|
|ePub File Size:||12.33 Mb|
|Price:||Free* [*Free Regsitration Required]|
Amazon Second Chance Pass it on, trade it in, give it a second life. Get fast, free shipping with Amazon Prime. Withstand a vacuum of at least 2 inches of mercury for 60 minutes, without loss of pressure. Law Districts Xwwa Drafting Files.
Hold water for one hour, without leakage after the tank has been filled with water to the top of the cover and let stand for 24 hours, then refilled to the top of the cover. All pipe connection openings to a tank shall be designed to allow connections in accordance with s. Alexa Actionable Analytics for the Web. The label shall be embossed, impressed, or securely attached to the tank. Register, May,No.
Register January No. Each treatment tank which has an anaerobic treatment compartment shall be labeled with a permanent label located near an inlet or outlet opening of the tank. All POWTS holding components or treatment components shall conform to the requirements of this section.
Except as provided in subd. A water treatment device which injects a water treatment compound into a water supply system shall maintain the compound concentration in the system over the working flow rate range and pressure range of the device.
Rules Indices Miscellaneous Archives Home. A water supply system shall be protected from backflow when unlisted water treatment compounds, which may affect the potability of the water, are introduced into the system. Where concrete tanks are required to have covers, the tanks shall meet one of the following requirements:.
Water supply outlets for human use or consumption may not be installed downstream of the introduction of an unlisted water treatment compound. Each aerobic treatment tank complying with NSF Standard 40 and listed by a nationally recognized ANSI accredited third party certified listing agency acceptable to the department shall be provided with 2 label plates.
Name or trademark of the manufacturer. Capacity of each compartment of the tank or the manufacturer’s model number. Amazon Advertising Find, attract, and engage customers. Withoutabox Submit to Film Festivals.
Wisconsin Legislature: SPS (2)
Amazon Aewa Digital Educational Resources. Updated on the first day of each month. Amazon Restaurants Food delivery from local restaurants. Nonpressurized point-of-use water heaters shall conform to ASSE Explore the Home Gift Guide. English Choose a language for shopping.
catalog – 160906 – page 228
Steel tank assemblies, including fittings and access openings, shall have a protective coating that will inhibit the deterioration of the steel due to internal and external environmental effects. The label shall include all of the following information:. Schedule Joint Senate Assembly Study.
Steel tanks that are required to have a cover shall be capable of withstanding one of the following requirements:. Entire code is always current. Amazon Rapids Fun stories for kids on the go. The Register date on each page is the date the chapter was last published. SPS to Steel tank assemblies, including fittings and access openings, aawa underground shall be cc707 with cathodic protection in accordance with UL Standard or STI-P 3.
Tanks constructed of materials other than concrete or steel that are not required to have a cover shall be capable of holding water after being filled to their inlet or outlet, whichever is higher, for one hour without loss of water. The interior of a concrete tank assembly, including fittings and access openings, shall have a protective coating or be constructed of material, above the lowest liquid level expected in the tank, that will inhibit the deterioration of the concrete due to internal environmental effects.
Tanks constructed of materials other than 7c07 or steel that are required to have a cover shall be capable of withstanding one of the following requirements:. Discover Prime Book Box for Kids. Extend to at least 4 inches above finished grade. Manhole openings over all anaerobic treatment apparatuses and pumps shall extend to at least 4 inches above finished grade.
A vacuum of at least 2 inches of mercury for 60 minutes, without loss of pressure. Tank assemblies, including fittings and access openings, shall be manufactured to be water tight as required under this subsection. ComiXology Thousands of Digital Comics.