E5CN/E5AN/E5EN Digital Temperature Controllers User’s Manual Basic Terminal block. E5CN. Basic Type. Analog input. Temperature input. safety standards, refer to your OMRON website. E5CN/E5AN/E5EN/E5GN Digital Temperature Controllers User’s Manual Basic Type (Cat. No. H). E5CN-H. Advanced Digital Temperature Controller (48 x 48 mm). E5CN-H between displaying the status of the Temperature Controller (auto/manual.
|Published (Last):||28 May 2013|
|PDF File Size:||6.96 Mb|
|ePub File Size:||15.84 Mb|
|Price:||Free* [*Free Regsitration Required]|
Doing so may occasionally result in electric shock, fire, or malfunction.
Page numbers refer to the previous version. Enter text from picture: Page 41 Tighten the screws to a torque of 0. Auto control will start when the input turns OFF.
The display changes as shown on the left for input types Input types 6, 8, 9, 10, 13, 14, 16,17, 18, 19, 20, 21, and 22 only: Press the U key to set the parameter to 8. PageAlarm 3 open in alarm: When a current value of If the heating characteristics and mmanual characteristics of the control object are very manuak and good control characteristics cannot be achieved with the same PID constants, the cooling coefficient can be used to adjust the propor- tional band P for the control output assigned to the cooling side.
PageScaling upper limit, Scaling lower limit, Decimal point initial setting level: Don’t show me this message again. Temperature Temperature Set value PageAlarm 2 latch: Note Heater voltage fluctuations are not considered here, so be take that into account when setting ee5cn detection current.
OMRON E5CN USER MANUAL Pdf Download.
Page operation level Standby sequence reset: PageAlarm 2 hysteresis: Function Monitor range Unit 0 to min or h Monitor No patent liability is assumed with respect to the use of the information contained herein. The follow- ing diagram shows the effect on data after passing through the digital fil- ter: PageAlarm 3 hysteresis: Setting a negative value produces an overlapping band.
The mode will be changed to the calibration mode, and adj will be displayed. Section Adjustment Level Adjustment Level This level is for executing AT auto-tuning and other operations, and for set control parameters.
Control output heating ; Control output 2: The input type must be set to tem- perature input. Page 9 Precautions for Safe Use Be sure to observe the following precautions to prevent operation failure, malfunction, or adverse affects on the performance and functions of the product. Wait band Set point Soak time This parameter monitors the set point during SP ramp operation.
Parameter Flow Starting in manual mode. Monitor range Unit Process value Input indication range See page Upper-limit alarm Lower-limit alarm A functional explanation is provided here for illustration, but models are not necessarily available for all possible combinations. Page Note Protection cannot be cleared or changed without the password.
When the manipulated variable turns OFF, the temperature begins to fall and the control turns ON again.